How to Clear Emergency Stop Alarm/Fault (E2800) in Air-Cooled Units
Why are you are getting this alarm?
- This error code will display on the controller screen when 1 or both of the auxiliary shut down switches is set to the off position.
- The switches were recently put on the units to meet code requirements in the event of an emergency needing the generator to be shutdown.
- For example, if the house is involved in a fire and the power goes out, that will make the generator start due to utility loss. If the lid is locked, there is no other access to the controller. So, for safety reasons, the switch located on the back of the unit can be set to the off position to stop the generator from running.
- Please note, for any reason the switch or switches are set to the "Off" position, giving the unit an active error code, this is NOT covered under warranty. Set the switch or switches to the on position and clear the code.
In order to clear the alarm you will need to do the following:
Open up the unit with the Generac key that was provided at time of installation, lid locks are on the left and right side of the unit
Once the unit is open you will see a control screen to the right side. This will show that you have an error code/ fault of E2800 emergency stop. In order to clear the alarm you will have to put the unit to "Off" position on the controller
Locate the 2 Auxiliary Shutdown switches, one inside the unit on the panel left of the controller and the other switch is on the rear outside panel nearest the controller end. Just below the lid hinge.
Make sure that both switches are shut off then back to the on position to ensure they are in the up position. Sometimes ice and hard rain will move them slightly and they just need to be reset.
Then press enter on the controller a few times and this should clear the fault. After should read either "Ready to Run" or "Run Hours (sequence of numbers)". Once the alarm has been cleared, press the ENTER key until the screen says "Ready to run" or "Run time hours are"(this means the error code has been cleared)
Set unit to manual (to make sure it runs)
Set unit to auto - and the error code has been cleared and should now say "Ready to run" It is now ready for the next utility outage.
Left Lid Lock Right Lid Lock
Evo Controller Inside Aux location Aux Switch Rear outside aux switch
How to clear emergency stop alarm/fault (E2800) in liquid cooled units
In order to clear the alarm you will need to do the following: 1. Locate the toggle switch, this is located on the side of the unit. (Examples below depicted in red) 2. Turn the switch to the upright position 3. On the same side the switch is located ...
What is considered “normal” oil consumption on air cooled generators?
Air Cooled engines are built with more tolerances for the block and rings to heat and cool or expand and contract. Because of this the engine will use more oil to cool the engine and also have some blow by in the rings due to the way the air cooled ...
What kind of oil do I use?
Required Oil per Generac's manuals for most air cooled engines is synthetic SAE 5W-30 for all temperature ranges. But please look at your specific region for average high and low temperatures. Verify proper type and quantity of engine oil prior to ...
Overloaded portable and now it does not start
If you had an overload and now it wont start, more than likely you may have flooded it out. I would pull the spark plug , clean and try to start. It may also need a maintenance depending on the hours of usage. if it doesn't start, do the proper ...
The UL label in the USA and the CUL label in Canada on electrical products indicate that the products have been designed, built and tested to be in accordance with safety standards for those respective countries by Underwriter Laboratories. The CUL ...